Viessmann Manufacturing Company Inc. recalls Viessmann Vitodens 200-W boiler models B2HB-45 and B2HB-57
2 March 2016
This is a joint recall with Health Canada, the United States Consumer Product Safety Commission (US CPSC), and Viessmann Manufacturing Company Inc. The recall involves Vitodens 200-W gas fired boiler models used for space or domestic hot water heating.
The recall states that the flue gas baffle used inside the heat exchanger assembly may become dislodged due to a mechanical fastener slipping, causing higher than normal flue gas temperatures to enter the flue gas collector and the venting system resulting in the F1 fault. The venting system may melt and cause the flue gases to escape into the house posing a risk of fire and increased carbon monoxide levels.
Viessmann Manufacturing has received 10 reports of incidents involving the boilers. Seven of these have been reported from Canada. No injuries have been reported in any of the incidents.
Read the complete recall from Health Canada.